150MW Power Plant
What You Need, Where You Need It
Scope of work
This project consists of design, supplying, and construction of 154 MW combined cycle power plants at ISO condition with a power factor of 0.8 (lagging-EPC) which is be constructed and commissioned in an area of < 29000 m².
The CCPP consists of two GTs that has 54 MW of nominal power at ISO condition and each is connected to a HRSG to produce steam for power generation purposes.
HRSG is of dual pressure type that produces high and low pressure steam and each pressure level consists of an economizer to preheat water before entering the drum, an evaporator to vaporize water and produce saturated steam and a super-heater to generate desired superheated steam to be delivered to induction section of the steam turbine. Pegging steam of deaerator is supplied by the LP steam Header.
Exhaust steam from the turbine outlet is cooled down through Air Cooled Condenser (ACC) before returning to the Condensate Receiving Tank (CRT). Condensate water from CRT outlet feeds the Condensate Extraction Pump (CEP) that is the start point of HRSGs.
Combined cycle power plant specifications